Shielded Twisted Single and Multi-Pair 300V fieldbus cable
UL Listed as PLTC Power Limited Tray Cable
UL Listed as ITC-HL - Instrument Tray Cable/Hazardous Location.
Type PLTC & Type ITC-HL for use in accordance with NEC articles 727 and 725
Single Pair passes IEEE 1202 vertical tray flame test.
Multi-Pairs pass the IEEE 383 and UL 13 vertical tray flame tests.
Sunlight Resistant 720hr per UL 1581
Oil resistance pre ICEA S-95-658.
-30C to 90C.
UL listed for direct burial.
Individual pairs are completely isolated.
100% Overall shield coverage.
Acceptable for use in NEC Class 1 Division 1 locations
CLX exceeds equipment grounding requirements of NEC Article 250.118 & 250.122
Conductor: #16AWG(1.3〖mm〗^2) tinned copper, Class B, stranded per ASTM B-8.
Insulation: Cross Linked Polyethylene(X-Olene) 37mils(0.94mm) nominal thickness, 90°C temperature rating per UL 13 and 2250.
Conductor Identification: Pigmented orange and blue in pairs, orange conductor numerically printed for group identification.
Pair Shield: Aluminum/Polyester tape overlapped to provide 100% coverage, and a Class B tinned copper drain wire, two sizes smaller than the conductor. Allmulti-pair shields are isolated from each other.
Multi-Pair Assembly: Pairs assembled with a left-hand lay. Cable fillers included where required to provide a round cable.
Multi-Pair Cable Shield: Aluminum/Polyester tape overlapped to provide 100% coverage, and a Class B strand tinned copper drain wire, same size asconductor.
Jacket: Orange, flame-retardant, PVC(Okoseal) per UL 13 and 2250. A rip cord is laid longitudinally under the jacket to facilitate removal.
C-L-X Sheath: A close-fitting, impervious, continuously welded and corrugated, aluminum sheath provides complete protection against moisture, liquids, and gases, has excellent mechanical strength, and provides equipment grounding through the sheath.
Outer Jacket: Orange, flame-retardant, Okoseal per UL 13 and 2250.
# Pairs Okonite Product Code